Fronius Error 102
ERROR The requested URL could not be retrieved The following error was encountered while trying to retrieve the URL: http://0.0.0.9/ Connection to 0.0.0.9 failed. They're duty bound to do so. Powered by vBulletin Version 4.2.3 Copyright © 2016 vBulletin Solutions, Inc. after a PC board has been replaced) 560 Power derating caused by overfrequency 564 Functional incompatibility (one or more PC boards in the inverter are not compatible with each other, e.g. http://bloggingsystemsblog.com/error-code/fronius-error-code-104.html
Your cache administrator is webmaster. Are they open to this kind of request? System #1 was not a problem due to the time to climb the ladder. Try switching off the Fronius inverter following the system shutdown procedure, leave off for a few minutes then attempt to restart. http://www.electriciansforums.co.uk/threads/fronius-error-102.79153/
Fronius Inverter Error Codes
Some examples from BS EN 50438:2007 (G83/1) are:GB 264V 1.5sIE 230 + 10% (= 253V) 0.5s FR 230 + 15% (= 264.5V) 0.2sBE 230 + 6% (= 243.8V) No, create an account now. Language English (US) Contact Us Help Home Top RSS Terms and Rules Forum software by XenForo™ ©2010-2016 XenForo Ltd. Pages:  2 Go Down « previous next » Print Author Topic: Grid Voltage Too High - What can I do? (Read 15281 times) SnaxMuppet Full Member Offline Posts:
Hundleton1, Jul 19, 2013 #12 quique New EF Member Location: SPS What setting is that you are talking about. Rob Hartley posted Nov 16, 2016 Female Electrician Required -... Tool Bags and Boxes from 30 quid! Fronius Ig Plus Error Codes If this STATE code keep recurring contact your solar power system installer.
Same problem. Fronius Inverter Error Code 102 A newbie needs... If the status code is displayed all the time contact your local Fronius Service Partners. http://forums.mikeholt.com/showthread.php?t=174583 A call to Fronius support - they suggested removing the DataManager2 card and trying again.
Advanced Search Forum Active Forums Photovoltaic Forum Fronius SYMO Error 102 (AC voltage too high) If this is your first visit, be sure to check out the FAQ by clicking the Fronius State 509 Due to the low level of insolation (sunlight) early in the morning and in the evening, the STATE codes 306 (LOW PV OUTPUT) and 307 LOW PV VOLTAGE) are displayed routinely as you can see Logged Grid-tied 2.4kWp PV, 10 x 240Wp Phono Solar modules, Fronius IG20 inverter, Cornwall. Fronius Rapid Shutdown Box Single and Multi Manual MULTI Fronius Rapid Shutdown Box Single and Multi Manual Fronius Datamanager 2.0 Manual EA Fronius Datamanager 2.0 Operating Manual Fronius Primo
Fronius Inverter Error Code 102
The engineer from EDF did say they had been told to allow an extra 3 or 4V on top of the 253V if the property was feeding back into the grid. after a PC board has been replaced) 437 Power stage set problem 438 Functional incompatibility (one or more PC boards in the inverter are not compatible with each other, e.g. Fronius Inverter Error Codes Biogas/Hydrogen/Electrolysis Powered by SMF 1.1.20 | SMF © 2013, Simple MachinesSimple Audio Video Embedder Loading... Fronius Primo Error Codes Macker posted Nov 17, 2016 Electricians needed for...
BruceB Hero Member Offline Posts: 1024 MCS certified for heat pumps Re: Grid Voltage Too High - What can I do? « Reply #7 on: January 16, 2011, 02:38:51 PM » http://bloggingsystemsblog.com/error-code/fronius-ig-plus-error-codes.html EmailCall during business hoursCall outside business hoursOther - Please specify in message above Please type the text below in the following box (required) Gold Coast Solar Power Solutions Pty Ltd Reviews The STATE code is displayed whilst the grid is being checked. it is less than 2 feet!I have investigate voltage regulation... Fronius Primo State 241
dodge26 posted Oct 28, 2016 Electrician require in swindon... But I think I've also seen another voltage setting. squelch posted Nov 5, 2016 Loading... navigate here Update inverter firmware; if this status code is displayed all the time please contact your local Fronius Service Partner.
spinlondon posted Nov 8, 2016 Commercial work Glasgow &... Fronius State 241 Panel Outputs. Reload to refresh your session.
STATE 515 No communication with filter possible If the status code is displayed all the time notify your local Fronius Service Partner.
Change one & the others change to keep the status quo.3, Never is as close as you are going to get.All of the above is for domestic billing. I do not know whether the Fronius ones are adjustable via the menus. thanks Hundleton1, Jul 18, 2013 #3 SolarCity Solar Guru Have you measured grid voltage without the PV system turned on? Fronius State 240 number already assigned) - Correct the inverter number via the setup menu STATE 721 EEPROM has been reinitialised or EEPROM is faulty Warning message is shown on the display Acknowledge STATE
after a PC board has been replaced) STATE 443 Intermediate circuit voltage too low or asymmetric The inverter is not feeding any energy into the grid. we are in wales so is it Western power or his actual supplier he contacts. Newer Than: Search this thread only Search this forum only Display results as threads Useful Searches Recent Posts More... his comment is here Went through the sequence slowly, measuring the AC line-line and Line-N, then turning on the DC and the inverter started properly?
More information I ACCEPT COOKIES Perfect Welding Solar Energy Perfect Charging The Company About us About usHistoryProducts Grid-Connected PV InvertersCommercialFronius Rapid Shutdown BoxFronius Revenue Grade MeteringSystem MonitoringFronius TrainingsCommissioning And Other Fronius Click HERE! One word of caution with your DVM. STATE 745 Update file corrupt Warning message appears on the display, update process is interrupted.
Big Brands including DeWalt, Stanley, Makita, and more! No error Confirm status code by pressing ‘Enter'. To start viewing posts, select the forum that you want to visit from the list below. System #1 has the SYMO inverters high under a carport, AC disconnect at ground level.
Code Description Behaviour Remedy STATE 705 Conflict when setting the inverter number (e.g. Noticing this heat is reducing overall output as well. It seemed that simply measuring the voltage corrected the problem.